SOLIS(8)

NAME
solis - Driver for Brazilian Microsol SOLIS UPS equipment

SYNOPSIS

solis -h

solis -a UPS_NAME [OPTIONS]

    Note

    This man page only documents the hardware-specific features of the solis driver. For information about the core driver, see nutupsdrv(8).

SUPPORTED HARDWARE

This driver has been tested with:

    • Solis 1000 VA

    • Solis 1500 VA

    • Solis 2000 VA

    • Solis 3000 VA

    • Back-UPS BZ1200-BR

    • Back-UPS BZ2200BI-BR

All Solis models are sinusoidal on-line.

In 2009, Schneider Electric acquired Microsol Technologies, and by 2012, the entire Microsol line of equipment was being sold under the APC brand. Newer devices may be better supported by microsol-apc(8) driver instead.

EXTRA ARGUMENTS

This driver support the following extra optional settings in the ups.conf(5).

battext=n
    Default = 0, no extra battery, where n = Ampere*hour.

prgshut=n
    Default = 0, no programmable shutdown; 1 to enable one.

COMMANDS

shutdown.return
    Shut down in .3 minutes and restart in .3 minutes after that.

shutdown.stayoff
    Shut down in .3 minutes and do not return.

ISSUES

The APC version of the Microsol protocol is slightly incompatible with the solis driver. As of version 0.62 of the solis driver, the driver will connect to the UPS, but some values are read incorrectly.

AUTHOR

Silvino B. Magalhães <sbm2yk@gmail.com>

SEE ALSO

  The core driver:

nutupsdrv(8)

  Driver for newer devices under same brand:

microsol-apc(8)

  Internet resources:

The NUT (Network UPS Tools) home page: https://www.networkupstools.org/historic/v2.8.3/